A current leak at any one of the outlets will trip the GFCI and cause all of the outlets connected to it to go dead. One device will usually be protecting several normal-looking outlets downstream from it. Hunting for a GFCI of unknown location takes some persistence, but it can often help to know the history of GFCI requirements in the National Electrical Code (NEC). The bathtub upstairs was slowly leaking for some time. Check This Out
These GFCI-protected outlets are supposed to be labeled (Photo 1), but the label often falls off. There is no way I'm going to try to fix this thing myself. But if you do have an electric heater, it must be fixed at a safe distance from the bath or shower. Occasionally a switch goes bad.
OK Free Newsletter Get timely DIY projects for your home and yard delivered right to your inbox every week! We’ll show you three common types of loose connections: loose terminal screws, loose stab-in connections, and loose wires at wire connectors. The switched item's neutral should attach to the corresponding neutral terminal: Load or Line. This pdf-chart expands this history even more.
By me moving the rice cooker sparks came from the wire. If someone added your now-dead GFCI unnecessarily when upgrading, the more original GFCI may have tripped somewhere ahead of this one. They had similar problems in 2 other outlet boxes. Gfci Outlet Not Resetting These will commonly make a hum or wheeze sound, for only for a few seconds at a time - not continuous unless leaking water 13) - city water system booster pump
If this still doesn’t resolve the problem, it’s time to call an electrician. ← Tame those cords! Bathroom Outlets Not Working No Gfci This wiring is dull gray, not the dull orange that's characteristic of copper. If you have a fusebox instead, one of the dryer's two fuses may be blown. http://www.doityourself.com/forum/electrical-ac-dc/413654-bathroom-outlets-not-working.html Our house was built in 1978 and one of the first things I did was add GFCI's to the bathrooms and outside, thinking these were unprotected.
This is probably its built-in safety "cutout" keeping the light from overheating. Outlets Not Working Breaker Not Tripped All light fittings, that are not enclosed, should be out of reach of someone using, or still wet from using, the bath or shower. Sign in to make your opinion count. I'm stumped!
This may be a visiting child, or it may be that when someone is unplugging something from the GFI, their thumb happens to press on the test button. [email protected] F. Bathroom Outlets Not Working But Lights Are When this has happened before, resetting the breaker switch fixed the problem. Bathroom Gfci Outlet Won't Reset Newsletter signup Get the latest updates from Electrical Safety First First name Last name Email address Sign up About Us Our Vision Our Board Work With Us Annual Report Grants And
Just that eventually you have to attach that aluminum to copper -------and therein the problem. http://dragonplayer.net/not-working/bathroom-switch-not-working.php And the breaker box isn't mark and I don't know which one to do, so I did all of them and they still Isn't . As for "breaker," the circuit-breaker-type GFCI does do double-duty as a normal circuit breaker and looks like a breaker and lives in a panel. Alan Clegg 46,223 views 28:15 Loading more suggestions... No Power In Bathroom Breaker Not Tripped
Working... No Gfci In Bathroom This wiring method is allowed by the electrical code, but it isn’t good practice since these stab-in connections can loosen over time and cause problems. This is understandable, but "circuit" is not the right word.
We've even tried the circuts of the apartments next door. Switch the circuit breaker off until you’ve located the problem. Photo 2: Check for loose wires Inspect the screw terminals for broken or loose wires. Electrical Outlet Not Working Breaker Not Tripped The reset buttons of newer GFIs (from 2003 on) will purposely not catch hold if they are not receiving power or are not hooked up right.
This method reduces the chance that a loose connection under a screw will cause a problem with other outlets on the circuit.Loose Wires at the Stab-in Connections As a timesaver The outlet had only facing left. If you have a house built before 1980, you may even want to check your bathroom receptacles. http://dragonplayer.net/not-working/bathroom-receptacle-not-working.php Only one of them has a GFCI, and it is not resetting.
Any ideas? A circuit for many of the locations requiring protection would naturally begin by going from the panel to a garage outlet, where the device itself would be placed. In either case, solving the problem requires additional electrical testing that we won’t cover here. Here's some more info if it changes anything: The complex is about 30 years old.
Depending on how the unit is wired, a GFCI in the kitchen could be protecting the bathroom and lights. To easily determine if your outlet problem results from a broken outlet or the appliance you are using, plug something else into the outlet. One unintentional condition would be where a ground wire is contacting the neutral side of a receptacle. I don't intend this site for giving advice on installation, but many people putting in a combination GFCI-switch device (GFCI outlet plus switch) seem to need help.
First, this chart summarizes troubleshooting the health of a GFI receptacle device: G F I S Y M P T O M CAUSE: Pushing test does not pop reset out Also look for broken, burned or corroded wires or screws Photo 3: Install a new outlet Install a new outlet by bending a loop in the ends of the hot, neutral It includes plugins for microwave and gas oven. Unless you feel uncomfortable doing minor repairs or don't understand that you should turn the electicity OFF before doing such installations...you can do the job yourself with a screwdriver and needle
Start by placing it against pipes and walls and floor in each room of the house - water sourced noise goes a long ways, and tends to reverberate in the walls, Another common practice has been to avoid giving protection to a refrigerator, since protecting it is not required. in AM before work. Sign in Share More Report Need to report the video?
danceswithcats02-12-2006, 11:39 PMRemember that a GFCI receptacle can be used to protect up to six downstream receptacles, and other circuits, such as a lighting circuit. vBulletin v3.8.7, Copyright ©2000-2016, vBulletin Solutions, Inc.